By now, the domestic hot water (DHW) supply system has been organized in compliance with the Latvian building normative LBN „Buildings’ Internal. These Regulations shall affirm the Latvian Construction Standard LBN with the Latvian Construction Standard LBN “Internal Water Main and . Construction normative LBN “External network for water Construction normative LBN “Internal water and sewage water.
|Published (Last):||21 November 2012|
|PDF File Size:||3.32 Mb|
|ePub File Size:||1.37 Mb|
|Price:||Free* [*Free Regsitration Required]|
Strategy of Energy Economy. The results evidence that this consumption and its usage indices correspond to the level achieved by Western in particular, North-European countries. In order to be able to connect hoses of mobile fire-fighting pumps, two pipes shall be provided from the penstock between the pumps at the isolation device of the sprinkler and drencher devices the diameter of which shall be 80 mm and which shall be fitted with check valves and the standard connections of fire-fighting hoses.
Fire taps shall be so installed that in the case of fire any point in the room could be extinguished with two spouts. A drencher device may have the following control function:. In stage work galleries it is permissible to connect fire taps to the upright tubes of the stage sprinkler system. If the capacity of the external water supply is not sufficient for the supply of the calculated amount of water for the elimination of fire or if the supply pipes are connected to the closed networksunderground reservoirs shall be created the volume of which shall ensure:.
The internal network of fire taps shall be a loop with two supply pipes from the external network, as well as with an isolation device for the sprinkler and drencher system.
EUR-Lex Access to European Union law
The methodology, which is in good agreement with the ideology of advanced management of DHS development, employs the ISO series of standards widely applied in the sphere of environment management.
Pressure in the fire taps located lbbn the boards of the stage shall ensure a compact water spout, which exceeds the distance from the boards to the coverings of the flies by two lbh. Additional energy saving in a building with improved insulation.
2211-98 of people on emergency evacuation routes in halls for public events. Issue 3 First Online: Buildings at cultural and entertainment institutions shall have the following fire-fighting equipment:. The primary emphasis was given to the hot water bln, with its noticeable daily fluctuations as well as changes caused by those in the inhabitants’ way of life. Table 8 Distance to the emergency exit Fire safety level of the building. Sign in to annotate. The goal of the authors was to clarify how the district heating system DHS development is affected by the heat consumption.
Republic of Latvia – səhifə 6
Dampers shall be installed for the main branch pipes having more than two fire taps. Household and drinking water supply pumps shall be installed on a vibration-insulating base and separated from the supply pipes and the internal lbh with flexible spacers. In the work, experimental results are presented that have been obtained through monitoring the hot water consumption. This circumstance changes considerably the input data for calculation of DHS elements, making it possible to work out appropriate measures in order to improve the DHS efficiency through step-by-step replacement of the elements with high energy loss.
In rooms located between staircases or exits to the outside. The Journals of Communal Services. The Cabinet of Ministers of 221-998 Republic of Latvia.
EUR-Lex – LLVA_ – EN – EUR-Lex
If the area of the boards of the stage is up to m 2three lgn taps shall be installedif the area is larger — four fire taps shall be installed and they may be open, without lockers.
If pressure in the external water supply cannot ensure the operation of fire-extinguishing installations, pumps shall be installed for the starting of which the following shall be used:. Number of people per 1 m of the width of the emergency route door if the volume of the hall is thousand m 3.
User Account Sign in to save searches and organize your favorite content. Issue 6-II Issue 6-I: Fire taps shall be installed:.
In rooms with exits to a dead-end corridor or hall. Isolating shut-off dampers in the network shall be so installed that 22198 are not more than two branches in the sector to be shut off.
Minister for Environmental Protection. Research Institute of the University of Central Florida. Drenchers for the stage portal and scenery safe shall be divided into two separate sections.
Budjko 1 and V. De Gruyter – Sciendo. Drencher devices shall be installed beneath the stage and proscenium fliesbeneath the lower work gallery level and the joints thereof, beneath the lower footpaths, as well as in the scenery safe and all stage passages including portal passages, pockets and proscenium and in the stage engine room.
DHS development ; environment management methods ; hot water consumption. The summary calculated water consumption shall be the largest of the following two internal fire-fighting system usages if:.